Tip & How-To about Xantrex Technology Electronics - Others
This information expands upon the error code information contained in the Link 2000 Owner?s Manual.
E-01 Inverter high DC/Battery voltage shutdown Battery voltage has risen above 15.5 VDC for 12-volt models or 31 VDC for 24-volt models.
E-02 Inverter low DC/Battery voltage shutdown Battery voltage has dropped below 10 VDC for 12-volt units or 20 VDC for 24-volt units.
E-03 Inverter or Charger overtemp shutdown Unit will reset automatically after it has cooled sufficiently.
E-04 Battery overload Caused by excessively discharged batteries. See section in inverter owner?s manual titled ?Charging overdischarged batteries.?
E-05 AC Backfeed AC power from an outside source has been fed to the AC output of the inverter. Potentially damaging to the unit. Disconnect incoming AC power and correct the situation.
E-06 Electronic Overload Inverter overload caused by too large a load or a short circuit. Reset by cycling power switch or connecting incoming AC power.
E-07 Triac control error Triac has overheated. Shut down unit and allow to cool.
E-08 High battery voltage shutdown during charge mode Check all charging sources for proper voltage. Reset by cycling the power switch.
E-10 Link 2000 de-powered This indicates that power was removed and restored to the Link 2000.
E-12 Battery #1 voltage sense leads open Blue wire is not connected to battery #1.
E-13 Battery #2 voltage sense leads open Violet wire is not connected to battery #2. E-14 Inappropriate Charged V selected for sensed voltage This value defaults to 13.2 for a 12-volt system, 26.4 for a 24-volt system. If this setting is above the voltage limits of the charging source, this error code will be displayed. Please refer to page 9 of the Link 2000 Owner?s Manual
E-15 Incoming AC polarity reversed Check incoming AC wiring for a reverse polarity condition.
CCC Indicates battery being charged. Displayed when Time remaining is selected. LO BAT More than 50% of declared capacity of battery 1 or battery 3 has been consumed.
OL Meter reading out of range U xx Designates a user setup CEF. Please read the sections pertaining to CEF on pages 19?22. A Designates Alternator output current on a Link 2000-R. is a number from 1?200. P Indicates Percent of charge mode selected. is a number from 1?100.
Posted by johnny... on
Trouble Code: P0722
A/T Pulse Generator 'B' Sensor Circuit Malfunction
Pulse generator 'B' (+) or (-) circuit is open or shorted to ground . Pulse generator 'B' is damaged or has failed. TCM has failed . TSB 01-40-006-1 (12/01) contains information about this code.
Trouble Code: P01529
Customer Snapshot Request Error
Transmission control module error. Check for trouble codes in the transmission control module. TSB 1-40-005 (3/01) contains information about this code. I have info. on these 2 codes,will search more for the others.
Aug 15, 2012 | 2000 Hyundai Accent
Jun 08, 2011 | HP : HP6L Laserjet Printer
Jun 04, 2011 | Vacuums
Dec 20, 2010 | Xantrex Technology Xantrex RS2000 Sine...
Apr 05, 2008 | Microwave Ovens
1,234 people viewed this tip
Usually answered in minutes!