20 Most Recent
Questions & Answers
Chronotherm III...Replace Battery notification
Thermostat problem; Honeywell chronotherm lll ' Low Batt. indicator Keeps blinking after Batteries replace. I chk'd batt. with elect. volt ntr. Was told to pull batt. and change ends with them , letthem stay reversed for 5-10 sec. then put them back in right order,and replace thermostat. No success!
Anyone have any answers
on Aug 28, 2014
Thermostat - Honeywell Chronotherm III
What you can do is try and clean the contacts. Open the door on the thermistat and remove the two screws, after that you can seperate the part that is mounted to the wall and the front panel. Look at the part that is mounted on the wall and you'll see the contacts that should be a copper color. They might be black from age. Clean them and you'll be surprised how well it will work after that.
on Nov 30, 2013
Automatic pilot light wont light on a honeywell furnace
Honeywell is a controls company and makes a variety of auto-pilots. If this is a no spark problem,does the lead from the igniter go to a big PC board or a module. If a module, check voltage to the spark module or thermostat voltage to the ignition module. If it comes from a large board, the board may be bad. I'll need more Info. if this does not cover it for you.
on Nov 23, 2013
Not finding what you are looking for?